The South Lift Station and Storage Tank project involved the design of a 1.0 MG storage tank, new pump station, and water line as well as improvements to the existing facility. Lamp Rynearson worked on coordinating these designs to allow the City to control the flow to and from the lift station. Our wastewater experts completed a draw down test that determined the 750 gpm pumps were operating at about 270 gpm.
Using Google Earth for the profile and desktop calculations, the system head was calculated, and correctly selected replacements pumps were specified and installed. The design included many components that reused existing infrastructure, allowing the project cost to come in under the anticipated budget.